For multi-location dimming, use up to nine Spacer System accessory dimmers with one Spacer System multi-location dimmer. Dimmers and accessory dimmers must have the same voltage rating. Not for use with mechanical 3-way or 4-way switches. Maximum traveller wiring run for multi-location appliations is 250' (76.2m). No derating required if ganged.