|Minimum Clearances -||Non-IC housings require minimum clearances of 3" from thermal insulation and 0.5" from adjacent building components.|
|Ceiling Thickness -||Ceiling thickness varies from 0.375" - 1.25" (remodels can accept 0.375" minimum ceiling thickness).|
|Lamp Adjustment -||Socket mounting plate allows slight adjustment to fine tune for best possible light distribution.|
|Installation -||New construction: Bar Hangers are adjustable from 13.625" to 24" and can be repositioned 90°.|
Remodel: High tension tempered steel springs secure remodel housings evenly to ceiling: hole cutout template provided for convenience.
|Junction Box -||Contains two 0.75", three 0.5" knockouts and four Romex pryouts with strain relief.|
|Electrical -||Quick connectors provided.|
|Listing -||UL Damp Location with Feed Through WSEC ASTM E283 for Air Tight (AT only).|